The correct specification, supply, fitting and maintenance are critical and it’s the responsibility of every person in the process to get it right.
It’s only when a fire breaks out that the consequences of poorly manufactured or fitted fire doors are known and sometimes it’s because the wrong type of ironmongery was used.
Components such as the hinges, closers, locks and latches are critical to making sure a fire door performs in a fire.
The ironmongery installed must be CE marked and CERTIFIRE approved and listed on the Door Fire Certificate to ensure performance.
Hinges must comply to the annex B of the BS EN 1935.
When fitted they should allow the fire door to close at any angle to which it has been opened.
We wouldn’t recommend using rising butt or spring hinges but instead a ball bearing or heavy-duty hinge that’s been recommended with the fire door.
When it comes to screws, the diameter of the screw plays a big role. If you’re installing a timber door, then your screw must be no less than 3.8mm (width) and 30mm (length). There must be a minimum of 3 screws on the hinge leaves.
Fire doors must close behind a person passing through at any angle. To comply with fire regulations, there’s two types of closers for non-latched doors.
Face-fixed overhead closers are fixed to the top of the door and come with a rated or adjustable strength to cater for different weights and sizes of doors.
Concealed door closers are hidden from view as they’re fitted within the door leaf and frame. They provide the same functionality as an overhead door closer but look cleaner as they can’t be seen.
Remember, you must get fit closers that are CE marked.
Locks and latches help provide an effective barrier to a fire, which is why they must be CE marked and comply with BS EN 12209. A fire door must remain closed within the frame and therefore a latch or lock will ensure this happens.
We recommend roller catches, rim latched, mortise latches and mortise locks. If you need to cut into the door to install a mortise lock, your gap should be the minimum necessary to prevent any voids where fire can enter.
Although it might sound scary, it’s simple. The components you use must be CE marked, CERTIFIRE approved and recommended with the fire door.
Although it’s not essential ironmongery, handles, knobs, letter boxes and spy holes must be fire resistant too.
We have a wide range of fire doors that are rated FD30 and FD60, plus a host of ironmongery to suit.
Speak to our Joinery Product Manager, Dominic Rice or one of his team in the Elliotts Sales Hub to find the right fire resistant products for your build. Call 023 8038 5385 or email email@example.com.